MGE Galaxy 3500. MGE Galaxy 3500. MGE Galaxy 5000. MGE Galaxy 3500. Batterys MGEUPS UPS. Battery pack for Ups MGEUPS Pulsar Ellipse 800. MGE Galaxy 3500. MGE Galaxy 3500. MGE Galaxy 5000. MGE Galaxy 3500. Batterys MGEUPS UPS. Battery pack for Ups MGEUPS Pulsar Ellipse 800.
Whether you’d like to monitor a single UPS or help with managing your entire virtualized network, Eaton has a monitoring and management software solution. From monitoring event history, notifying you of alerts and delivering real-time status, Eaton software provides the tools you need to keep your critical equipment running at all times. Our software solutions are easy to use and maintain business continuity which saves time, saves money and reduces risk.
Use the drop down menus below to select a specific product to see related software and firmware solutions or filter the results using the “solution type” drop down to show only software, firmware or legacy software.
Or select your software solution:
View a complete listing of our software & firmware products
mge-shut - Driver for SHUT Protocol UPS equipment
mge-shut -a UPS_NAME [OPTIONS]Note
This man page only documents the hardware-specific features of the mge-shut driver. For information about the core driver, seenutupsdrv(8).
mge-shut supports all recent Eaton, MGE and Dell UPS models which use the SHUT (Serial HID UPS Transfer) protocol.
Older MGE models, such as Pulsar ESV+, Pulsar EX and Pulsar ES+, use the U-Talk protocol and should use the mge-utalk driver.
This driver also supports the following optional settings:
lowbatt=numSet the low battery warning threshold at which shutdown is initiated by upsmon(8).
The factory default value is 30 (in percent), and can be settable depending on the exact model.
The default value is 20 (in seconds). Usually this must be lower than ondelay, but the driver will not warn you upon startup if itisn't.
The default value is 30 (in seconds). Usually this must be greater than offdelay, but the driver will not warn you upon startup if it isn't.Some UPS'es will restart no matter what, even if the power is (still) out at the moment this timer elapses. In that case, you could try if setting ondelay =-1 in ups.conf helps.
ondelay parameter was set in ten seconds unit in the legacy mge-shut driver ( 3 for 30 seconds) . It is now set in seconds ( 30 for 30 seconds). Make sure youuse the correct unit in your configuration.
This argument is ignored. It is only here for backward compatibility.
Repetitive timeout and stalenessSome models tends to be unresponsive with the default polling frequency. The result is that you have some 'data stale' errors in your system log.
In this case, simply modify the general parameter 'pollinterval' to a higher value (like 10 for 10 seconds). This should solve the issue.
Using notification=3 might also help.
The core driver
- Ups Battery Price
- Ups Battery Wikipedia(8)